Remote Monitoring Systems
There are various control modules used in generators. Different communication ports are available on these modules according to the property of the module. Monitoring up to only 10 mt can be performed by some modules while remote monitoring can be performed by some. At this point, communication properties of control module have importance. Below mentioned communication properties and external communication modules used vary by the brand of the module used.
Mode of generator monitoring is classified into three categories:
1-b- Cabled monitoring up to a distance of 100 mt to the generator. (RS-485 communication protocol- RS485-Usb converter is needed in addition to the computer to be monitored.)
1-c-Wireless remote access through GSM modem (GSM should be available in addition to both control module and the computer to be monitored).
1-d-Monitoring through Ethernet line (It is suitable for monitoring up to 100 mt in cabled form or remote monitoring through Ethernet network.)
1-e-Process of sending message to mobile phone through GSM modem in case of failure.
2-b-This is the process of the possibility of simultaneously monitoring the generators that feed the system in multiple synchronization on a single screen through Ethernet, GSM Modem or in cabled form up to 100 mt ( All parameters of generators can be accessed, parameters can be changed, generators can start/stop, they can be put in synchronicity and taken out)
2-c- This is the system of monitoring the generators that feed the system in multiple synchronization through RS-485 protocol on an individual basis. (All parameters of generators can be accessed, parameters can be changed, generators can start/stop, they can be put in synchronicity and taken out)